K20-120V2Y | K20-220V2Y | K20-380V2Y |
PDF files you need to download the
1. As the compact size, it is endured big surge.
2. Can be directly installed at the distribution panel.
3. Excellent reponse without delay in opreation
to abrupt surge.
4. Low clamping voltage to get definite protection effects.
5. Service life is not vaild in excessive surge.
1. Endurance of surge.
2. Protect rallway signal device.
3. Protect the broadcasting relay station
4. Lightening surge meaure for water facility.
5. Protect communication instrumentation and controling device.
6. Protect automatic control device of distribution cord.
7. Escalator, elevator Control panel protection.
8. Input low voltage, distributing box Used in the main
incoming power supply.
9. UPS input/ out put, CCTV, DCS, PLC. SCADA.
10. VMS electronic display, SERVICE ENTERANCE.
11. Used in train, subway network, communication base stations.
12. Used in manufacturing machine, industrial computer panel.
13. Fence detection system power, solar power system.
14. Use in farm, department store, playgrounds, bank, hospital,
manufacturing plant, Museum, telegraph telephone company,
power plant, oil refinery plant.
Petrol station, chemical plants, nuclear powered plants.
* Single phase + E phase
■ Specifications and standards are subject to change without prior notice.
■ The special model could be made by your order.
We recommed the following measures since there is a risk of short or destruction when surge substantiallyexceeding the rating penetrates into the arrestor.
- install the arrestor closer to the device than the overcurrent protection device A (breaker, leakage, breaker fuse, etc.) circuit
and immediately separate it from the power when it is shorted.
- install the overcurrent protection device at B if it cannot be installed at A.
- Use leakage circuit breaker at A or install the C heat-response temperature fuse
if the arrestor is grounded on the device case or fully low earth resistance cannot be obtained.
Check whether it is within the usage scope of rating temperature
when using it near direct sunlight or heat element.
- Pit in the protection cover when you must use it in the place with dust, iron dust,
exposed to rain or dew or likely to have problem of salt pollution.
(Use protection cover)
- Use 600V vinyl resistance cord(IV cord), 2㎟ or equovalent for wiring of arrestor.(over 5.5㎟ in case of earth line)Wiring of arrestor should be as straight and short as possible.
- Use the arrestor with surge endurance of 20,000A for the measurement of electricity facility induction lightening surge.
1. Turn off the power when SPD is installed.
2. As the shorter length of wire, better the protective performance.
3. Please check Distributing box, UPS, AVR protection equipment's voltage and ground cable and
please install as soon as possible where it needed.
4. Once the installment is finished, turn on the power.
5. Lamp is light up when power on, the installment is done properly.
(If the status light didn't turn on, please lower crossing gate to check length of wire connection.)